// CODE SNIPPET
1216.6 Steam-Distribution Piping
JUMP TO FULL CODE CHAPTER
Where multi-row elements are installed in an enclosure, they shall be top fed and piped in parallel down to the steam trap. A single steam trap for each row of heating elements shall be installed. Where the size of the return header is increased by a minimum of one pipe size, a single steam trap shall be permitted to be installed for multiple rows. Where multiple steam unit heaters are installed, an individual steam trap for each unit shall be installed.
Related Code Sections
1216.6 Hydronics, Steam-Distribution Piping
Where multi-row elements are installed in an enclosure, they shall be top fed and piped in parallel down to the steam trap. A single steam trap ...
Uniform Mechanical Code 2018 of Nevada > 12 Hydronics > 1216.0 Steam Systems > 1216.6 Steam-Distribution Piping
210.0 Definitions, — H —
air-distribution ducts and fans, and all steam and hot water piping, together with all control devices and accessories installed as part ...
2.5-3.5 Building Systems, HVAC Air Distribution
of the humidifier to ensure complete moisture absorption. Steam humidifiers shall be used. Use of reservoir-type water spray or evaporative pan ...
Guidelines for Design and Construction of Residential Health, Care, and Support Facilities 2018 of Nevada > 2.5 Building Systems > 2.5-3 Heating, Ventilation, and Air-Conditioning (HVAC) Systems > 2.5-3.5 HVAC Air Distribution
1310.4 Health Care Facilities and Medical Gas and Medical Vacuum Systems, Location of Piping
Piping risers shall be permitted to be installed in pipe shafts if protected from physical damage, effects of excessive heat, corrosion, or contact ...
Uniform Plumbing Code 2018 of Nevada > 13 Health Care Facilities and Medical Gas and Medical Vacuum Systems > 1310.0 Installation of Piping > 1310.4 Location of Piping