// CODE SNIPPET
502.4 Stationary Lead-Acid Battery Systems
JUMP TO FULL CODE CHAPTER
The ventilation system shall be designed to limit the maximum concentration of hydrogen to 1.0 percent of the total volume of the room.
Related Code Sections
502.4 Exhaust Systems, Stationary Lead-Acid Battery Systems
Ventilation shall be provided for stationary lead-acid battery systems in accordance with this chapter and Section 502.4.1 or 502.4.2 ...
NYC Mechanical Code 2008 > 5 Exhaust Systems > 502 Required Systems > 502.4 Stationary Lead-Acid Battery Systems
907.2.20.1 Fire Protection Systems, Battery Rooms
An approved automatic smoke detection system shall be installed in areas containing stationary lead-acid battery systems having a liquid capacity ...
NYC Building Code 2008 > 9 Fire Protection Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required > 907.2.20 Covered Mall Buildings > 907.2.20.1 Battery Rooms
508.2.1 General Building Heights and Areas; Separation of Occupancies, Occupancy Classification
lead-acid battery systems having a liquid capacity of more than 100 gallons used for facility emergency power or uninterrupted power supplies ...
NYC Building Code 2008 > 5 General Building Heights and Areas; Separation of Occupancies > 508 Incidental Use Areas and Mixed Occupancies > 508.2 Incidental Use Areas > 508.2.1 Occupancy Classification
502.4 Exhaust Systems, Stationary Storage Battery Systems
Stationary storage battery systems, as regulated by Section 608 of the New York City Fire Code , shall be provided with ventilation in accordance ...
NYC Mechanical Code 2014 > 5 Exhaust Systems > 502 Required Systems > 502.4 Stationary Storage Battery Systems
502.5 Exhaust Systems, Valve-Regulated Lead-Acid Batteries
Valve-regulated lead-acid battery systems as regulated by the New York City Fire Code, shall be provided with ventilation in accordance ...
NYC Mechanical Code 2008 > 5 Exhaust Systems > 502 Required Systems > 502.5 Valve-Regulated Lead-Acid Batteries