// CODE SNIPPET
42.8.5 Specific Requirements for LP-gas Dispensing Devices
JUMP TO FULL CODE CHAPTER
Dispensing devices for LP-Gas shall be located as follows:
- At least 10 ft (3 m) from any dispensing device for Class I liquids
- At least 5 ft (1.5 m) from any dispensing device for Class I liquids where the following conditions exist:
Related Code Sections
42.8.5 Refueling, Specific Requirements for LP-gas Dispensing Devices
Dispensing devices for LP-Gas shall meet all applicable requirements of Chapter 69 and NFPA 58. [ 30A: 12.5.1 ...
Fire Code 2018 of West Virginia > 42 Refueling > 42.8 Additional Requirements for CNG, LNG, Hydrogen, and LP-gas > 42.8.5 Specific Requirements for LP-gas Dispensing Devices
(3) Special Occupancies, Fuel Storage
) locations. [ 30A: 12.4] (f) Specific Requirements for LP-Gas Dispensing Devices. [ 30A: 12.5] Dispensing devices for LP-Gas shall be located as follows ...
National Electrical Code 2017 of West Virginia > 5 Special Occupancies > 514 Motor Fuel Dispensing Facilities > 514.3 Classification of Locations > (B) Classified Locations > (3) Fuel Storage
42.2 Refueling, Automotive Fuel Servicing
facilities where only liquefied petroleum gas (LP-Gas), liquefied natural gas (LNG), or compressed natural gas (CNG) is dispensed as motor fuel ...
18.104.22.168 Refueling, Plans and Specifications
equipment, including emergency fuel shutdown devices Specifications for fuel storage and venting components Other information as required ...
Fire Code 2018 of West Virginia > 42 Refueling > 42.2 Automotive Fuel Servicing > 42.2.2 General Requirements > 22.214.171.124 Plans and Specifications
Section 412 Gas Piping Installations, (IFGC) Liquefied Petroleum Gas Motor Vehicle Fuel-Dispensing Facilities
vehicle. The requirements for self-service LP-gas dispensing systems shall be in accordance with the following: The arrangement and operation ...
Fuel Gas Code 2015 of West Virginia > 4 Gas Piping Installations > 412 (IFGC) Liquefied Petroleum Gas Motor Vehicle Fuel-Dispensing Facilities