// CODE SNIPPET
1910.106(g)(6)(iii) Special Room
JUMP TO FULL CODE CHAPTER
Heating equipment may be installed in a special room separated from an area classified by Table H-19 by walls having a fire resistance rating of at least 1 hour and without any openings in the walls within 8 feet of the floor into an area classified in Table H-19. This room shall not be used for combustible storage and all air for combustion purposes shall come from outside the building.