// CODE SNIPPET
[F] 403.4.8.1 Special Requirements for Standby Power Systems
JUMP TO FULL CODE CHAPTER
If the standby system is a generator set inside a building, the system shall be located in a separate room enclosed with 2-hour fire barriers constructed in accordance with Section 707 or horizontal assemblies constructed in accordance with Section 711, or both. System supervision with manual start and transfer features shall be provided at the fire command center.