// CODE SNIPPET
909.18.8 Special Inspections for Smoke Control
JUMP TO FULL CODE CHAPTER
Smoke control systems shall be tested by a special inspector.
Special inspections shall be conducted in accordance with the following:
- During erection of ductwork and prior to concealment for the purposes of leakage testing and recording of device location.
- Prior to occupancy and after sufficient completion for the purposes of pressure-difference testing, flow measurements, and detection and control verification.
Special inspection agencies for smoke control shall have expertise in fire protection engineering, mechanical engineering and certification as air balancers.
A complete report of testing shall be prepared by the special inspector or special inspection agency. The report shall include identification of all devices by manufacturer, nameplate data, design values, measured values and identification tag or mark. The report shall be reviewed by the responsible registered design professional and, when satisfied that the design intent has been achieved, the responsible registered design professional shall seal, sign and date the report.
A copy of the final report shall be filed with the fire code official and an identical copy shall be maintained in an approved location at the building.