// CODE SNIPPET
1705.17 Special Inspection for Smoke Control
JUMP TO FULL CODE CHAPTER
Smoke control systems shall be tested by a special inspector.
The test scope shall be as follows:
- During erection of ductwork and prior to concealment for the purposes of leakage testing and recording of device location.
- Prior to occupancy and after sufficient completion for the purposes of pressure difference testing, flow measurements and detection and control verification.