// CODE SNIPPET
2113.9.2 Spark Arrestors
JUMP TO FULL CODE CHAPTER
Where a spark arrestor is installed on a masonry chimney, the spark arrestor shall meet all of the following requirements:
- The net free area of the arrestor shall be not less than four times the net free area of the outlet of the chimney flue it serves.
- The arrestor screen shall have heat and corrosion resistance equivalent to 19-gage galvanized steel or 24-gage stainless steel.
- Openings shall not permit the passage of spheres having a diameter greater than 1/2 inch (12.7 mm) nor block the passage of spheres having a diameter less than 3/8 inch (9.5 mm).
- The spark arrestor shall be accessible for cleaning and the screen or chimney cap shall be removable to allow for cleaning of the chimney flue.