// CODE SNIPPET
4805.3 Solid-Ceiling Sets and Platforms
JUMP TO FULL CODE CHAPTER
All interior solid-ceiling sets over 600 square feet (55.7 m2) in area, and platforms (when provided) over 600 square feet (55.7 m2) in area and which exceed 3 feet (914 mm) in height shall be protected by one of the following:
- An approved and listed heat detector system. Heat detectors shall be spaced 30 feet (9144 mm) on center or as required by the manufacturer's installation instructions. Detectors shall be connected to an approved and listed central, proprietary or remote station service or a local alarm, which will give an audible signal at a constantly attended location. Such system shall be installed in accordance with Chapter 9.
- The ceiling shall be positioned to allow for the operation of the building's automatic fire sprinkler system after rehearsal, videotaping, filming, or broadcasting of programs has been completed for the day.
- An approved fire watch.
- Special hazards shall be reviewed by the fire code official (see Additional Fire Protection Systems, Section 901.4.3).