// CODE SNIPPET
909.1.1 Smoke Control System Maintenance
JUMP TO FULL CODE CHAPTER
A written maintenance program, including periodic inspection and testing, shall be established and implemented immediately upon installation of the smoke control system.
A logbook or other approved form of recordkeeping documenting each inspection and test shall include the date of the maintenance, identification of servicing personnel, description of any operating defects or deficiencies, notifications made, corrective action taken, including parts replaced, and/or other information prescribed by the department by rule.
Operational testing of the smoke control system shall include all components of the system, including initiating devices, fans, dampers, controls, doors and windows. Dedicated smoke control systems shall be tested semiannually. Nondedicated smoke control systems shall be tested annually. All systems shall be tested under both normal power and emergency power.