188.8.131.52.2 Sleeping Suites
(B)* Sleeping suites shall be arranged in accordance with one of the following:
- *Patient sleeping rooms within sleeping suites shall provide one of the following:
- The patient sleeping rooms shall be arranged to allow for direct supervision from a normally attended location within the suite, such as is provided by glass walls, and cubicle curtains shall be permitted.
- Any patient sleeping rooms without the direct supervision required by 184.108.40.206.2.1(B)(1)(a) shall be provided with smoke detection in accordance with Section 9.6 and 18.3.4.
- Sleeping suites shall be provided with a total (complete) coverage automatic smoke detection system in accordance with 220.127.116.11 and 18.3.4.
(B) Sleeping suites shall not exceed 7500 ft2 (700 m2), unless otherwise provided in 18.104.22.168.2.3(C).
(A) Travel distance between any point in a sleeping suite and an exit access door to another suite, an exit access corridor door, or a horizontal exit door from that suite shall not exceed 100 ft (30 m).