// CODE SNIPPET
E3609.5 Sizing Bonding Jumper on Supply Side of Service and Main Bonding Jumper
JUMP TO FULL CODE CHAPTER
The bonding jumper shall not be smaller than the sizes shown in Table E3603.1 for grounding electrode conductors. Where the service-entrance conductors are paralleled in two or more raceways or cables, the equipment bonding jumper, where routed with the raceways or cables, shall be run in parallel. The size of the bonding jumper for each raceway or cable shall be based on the size of the service-entrance conductors in each raceway or cable.