// CODE SNIPPET
A105.0 Size of Building Supply
JUMP TO FULL CODE CHAPTER
Knowing the permissible friction loss per 100 feet (30 480 mm) of pipe and the total demand, the diameter of the building supply pipe shall be permitted to be obtained from Chart A105.1(1), Chart A105.1(2), Chart A105.1(3), Chart A105.1(4) Chart A105.1(5), Chart A105.1(6), or Chart A105.1(7), whichever is applicable. The diameter of pipe on or next above the coordinate point corresponding to the estimated total demand and the permissible friction loss will be the size needed up to the first branch from the building supply pipe.
Chart A105.1(2) shall be used for ferrous pipe with the most favorable water supply in regards to corrosion and caking. Where the water is hard or corrosive, Chart A105.1(3) or Chart A105.1(4) will be applicable. For extremely hard water, it will be advisable to make additional allowances for the reduction of the capacity of hot-water lines in service.