// CODE SNIPPET
C 304.2 Size of Building Drain and Building Sewer
Go To Full Code Chapter
The maximum number of drainage fixture units allowed on the building drain or building sewer of a given size shall be in accordance with Table C 304.2. The size of a building drain or building sewer serving a water closet shall be not less than 3 inches (80 mm).
|DIAMETER OF PIPE
|MAXIMUM NUMBER OF DRAINAGE FIXTURE UNITS FOR SANITARY BUILDING DRAINS AND RUNOUTS FROM STACKS|
|SLOPE (inches per foot)|
|15||7000||8300||10 000||12 000|
For SI units: 1 inch = 25 mm, 1 inch per foot = 83.3 mm/m
1 On-site sewers that serve more than one building shall be permitted to be sized according to the current standards and specifications of the administrative authority for public sewers.
2 A maximum of two water closets or two bathroom groups, except in single-family dwellings, where a maximum of three water closets or three bathroom groups shall be permitted to be installed.
Related Code Sections
C 304.2 Alternate Plumbing Systems, Size of Building Drain and Building Sewer
The maximum number of drainage fixture units allowed on the building drain or building sewer of a given size shall be in accordance with Table C ...
717.0 Sanitary Drainage, Size of Building Sewers
The minimum size of a building sewer shall be determined on the basis of the total number of fixture units drained by such sewer, in accordance ...
C 601.9 Alternate Plumbing Systems, Sizing Building Drains and Sewers
In a single-stack vent system, the building drain and branches thereof shall be sized in accordance with Table 703.2, and the building sewer shall ...
P3005.4 Sanitary Drainage, Drain Pipe Sizing
and stacks by equating the assigned d.f.u. values to pipe sizes shown in Table P3005.4.1. Determine the pipe diameter and slope of the building drain ...
710.5 Sanitary Drainage, Size of Building Drains and Sewers
Building drains or building sewers receiving a discharge from a pump or ejector shall be adequately sized to prevent overloading. Two fixture units ...