Design, construction, and installation of exterior security lighting for educational and ancillary facilities shall be provided for:
Auto, bus, and service drives and loading areas.
Covered and connector walks between buildings and between buildings and parking.
Parking area lighting standards shall be designed to withstand appropriate wind loads. Parking areas shall be illuminated to an average maintained horizontal footcandle, measured at the surface as follows:
Parking areas—1 footcandle (10 lux).
Covered and connector walks—1 footcandle (10 lux).
Building exteriors, perimeters, and entrances may be illuminated to the minimum number of footcandles, measured at the surface with a suggested uniformity ratio of 2:1 as follows:
Entrances—5 footcandles (50 lux).
Building surrounds—1 footcandle (10 lux).
Exterior lighting shall be shielded from adjacent properties.