// CODE SNIPPET
18.104.22.168 Signal Devices Remote From Controller
JUMP TO FULL CODE CHAPTER
Where the pump room is not constantly attended, audible or visible signals powered by a source other than the engine starting batteries and not exceeding 125 V shall be provided at a point of constant attendance. [20:22.214.171.124]
The remote panel shall indicate the following:
- The engine is running (separate signal).
- The controller main switch has been turned to the off or manual position (separate signal).
- * There is trouble on the controller or engine (separate or common signals). (See 126.96.36.199.4 and 188.8.131.52.5.)
Related Code Sections
184.108.40.206 Fire Protection Systems, Signal Devices Remote From Controller
] Controllers shall be equipped to operate circuits for remote indication of the conditions covered in 220.127.116.11.3 ...
Fire Code 2018 of West Virginia > 13 Fire Protection Systems > 13.4 Fire Pumps > 13.4.5 Components > 18.104.22.168 Signal Devices Remote From Controller
Section E4301 Class 2 Remote-Control, Signaling and Power-Limited Circuits, General
circuits that are not an integral part of a device or appliance. Other classes of remote-control, signaling and power-limited conductors shall comply ...
Residential Code 2015 of West Virginia > 43 Class 2 Remote-Control, Signaling and Power-Limited Circuits > E4301 General
(A) Special Occupancies, Emergency Electrical Disconnects
the dispensing devices; to all associated power, control, and signal circuits; and to all other electrical equipment in the hazardous (classified) locations ...
National Electrical Code 2017 of West Virginia > 5 Special Occupancies > 514 Motor Fuel Dispensing Facilities > 514.11 Circuit Disconnects > (A) Emergency Electrical Disconnects
725.1 Special Conditions, Scope
This article covers remote-control, signaling, and power-limited circuits that are not an integral part of a device or of utilization equipment ...
National Electrical Code 2017 of West Virginia > 7 Special Conditions > 725 Class 1, Class 2, and Class 3 Remote-Control, Signaling, and Power-Limited Circuits > 725.1 Scope