// CODE SNIPPET
210.62 Show Windows
Related Code Sections
210.62 Wiring and Protection, Show Windows
At least one 125-volt, single-phase, 15- or 20-ampererated receptacle outlet shall be installed within 450 mm (18 in.) of the top of a show window ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 210 Branch Circuits > 210.62 Show Windows
(G) Wiring and Protection, Show Windows
Show windows shall be calculated in accordance with either of the following: The unit load per outlet as required in other provisions ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 220 Branch-Circuit, Feeder, and Service Load Calculations > 220.14 Other Loads — All Occupancies > (G) Show Windows
410.14 Equipment for General Use, Luminaires in Show Windows
Chain-supported luminaires used in a show window shall be permitted to be externally wired. No other externally wired luminaires shall be used ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.14 Luminaires in Show Windows
400.15 Equipment for General Use, In Show Windows and Showcases
Flexible cords used in show windows and showcases shall be Types S, SE, SEO, SEOO, SJ, SJE, SJEO, SJEOO, SJO, SJOO, SJT, SJTO, SJTOO, SO, SOO, ST ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 400 Flexible Cords and Flexible Cables > 400.15 In Show Windows and Showcases