// CODE SNIPPET
220.43 Show-Window and Track Lighting
JUMP TO FULL CODE CHAPTER
For track lighting in other than dwelling units or guest rooms or guest suites of hotels or motels, an additional load of 150 volt-amperes shall be included for every 600 mm (2 ft) of lighting track or fraction thereof. Where multicircuit track is installed, the load shall be considered to be divided equally between the track circuits.
Exception: If the track lighting is supplied through a device that limits the current to the track, the load shall be permitted to be calculated based on the rating of the device used to limit the current.
Related Code Sections
220.43 Wiring and Protection, Show-Window and Track Lighting
For show-window lighting, a load of not less than 660 volt-amperes/linear meter or 200 volt-amperes/linear foot shall be included for a show window ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 220 Branch-Circuit, Feeder, and Service Load Calculations > 220.43 Show-Window and Track Lighting
(A) Equipment for General Use, Lighting Track
Lighting track shall be permanently installed and permanently connected to a branch circuit. Only lighting track fittings shall be installed ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.151 Installation > (A) Lighting Track
210.62 Wiring and Protection, Show Windows
At least one 125-volt, single-phase, 15- or 20-ampererated receptacle outlet shall be installed within 450 mm (18 in.) of the top of a show window ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 210 Branch Circuits > 210.62 Show Windows
801.7 Interior Finishes, Windows
Show windows in the exterior walls of the first story above grade plane shall be permitted to be of wood or of unprotected metal framing ...