Shade/green houses shall be of Type I or II construction (metal frame) capable of withstanding the appropriate wind load.
The location of the shade/green house shall not hinder exiting from new and/or existing structures.
A minimum of two doors remotely located shall be provided. Doors shall be sidehinged and shall swing in the direction of egress.
Green houses shall meet accessibility requirements. The accessible walkway shall be connected to doors leading to an accessible route to the permanent structure.
Shade cloth shall be tear-away fabric securely fastened to the structural frame.
A minimum of one Type 2A- 10B:C fire extinguisher shall be provided per shade/green house.
Fire alarm pull stations shall be located within 200 feet (60 960 mm) of any shade or green house. Fire alarm horns mounted on a permanent building must be audible inside the shade/green house.
Space heaters, when provided, shall be mounted at least 6 feet 8 inches (2031 mm) AFF.