// CODE SNIPPET
453.19 Shade and Green Houses
JUMP TO FULL CODE CHAPTER
Shade/green houses shall be of Type I or II construction (metal frame) capable of withstanding the appropriate wind load.
A minimum of two doors remotely located shall be provided. Doors shall be side hinged and shall swing in the direction of egress.
Green houses shall meet accessibility requirements. The accessible walkway shall be connected to doors leading to an accessible route to the permanent structure.
Shade cloth shall be tear-away fabric securely fastened to the structural frame.
A minimum of one Type 2A-10B:C fire extinguisher shall be provided per shade/green house.
Fire alarm pull stations shall be located within 200 feet (60 960 mm) of any shade or green house. Fire alarm notification appliances mounted on a permanent building must be audible inside the shade/green house.
Space heaters, when provided, shall be mounted at least 6 feet 8 inches (2031 mm) AFF.