// CODE SNIPPET
1105.2 Setback Roofs
JUMP TO FULL CODE CHAPTER
Drains on setback roofs shall be permitted to be connected to the controlled-flow drainage systems provided:
- The setback is designed for storing water, or
- The square footage of the setback drainage area is converted as outlined in Section 1105.0 to gpm, and the storm-water pipe sizes in the controlled-flow system are based on the sum of the loads.
- The branch from each of the roof drains that are not provided with controlled flow shall be sized in accordance with Table 1103.1.
Related Code Sections
1105.2 Storm Drainage, Setback Roofs
Drains on setback roofs shall be permitted to be connected to the controlled-flow drainage systems provided: The setback is designed for storing ...
Uniform Plumbing Code 2018 of Nevada > 11 Storm Drainage > 1105.0 Controlled-Flow Roof Drainage > 1105.2 Setback Roofs
R324.6.2 Building Planning, Setback at Ridge
For photovoltaic arrays occupying not more than 33 percent of the plan view total roof area, not less than an 18-inch (457 mm) clear setback ...
Residential Code 2018 of Nevada > 3 Building Planning > R324 Solar Energy Systems > R324.6 Roof Access and Pathways > R324.6.2 Setback at Ridge
220.127.116.11.2 Heating, Ventilating, and Air Conditioning, Setback Controls
humidity levels. Exception to 18.104.22.168.2 Radiant heating systems capable of and configured with a setback heating set point at least 4°F ...
Energy Standard for Buildings Except Low-Rise Residential Buildings 2016 of Nevada > 6 Heating, Ventilating, and Air Conditioning > 6.4 Mandatory Provisions > 6.4.3 Controls and Diagnostics > 22.214.171.124 Off-Hour Controls > 126.96.36.199.2 Setback Controls