// CODE SNIPPET
(1) Services and On-Site Power Production Facilities
JUMP TO FULL CODE CHAPTER
Service conductors and conductors supplied by on-site power production facilities shall be physically routed outside a building(s) and shall be installed as service-entrance conductors in accordance with 230.6, 230.9, and Parts III and IV of Article 230. Where supply conductors cannot be physically routed outside of buildings, the conductors shall be permitted to be routed through the building(s) where installed in accordance with 230.6(1) or (2).
Exception: The supply conductors within the fire pump room shall not be required to meet 230.6(1) or (2).
Related Code Sections
(1) Special Equipment, Services and On-Site Power Production Facilities
Service conductors and conductors supplied by on-site power production facilities shall be physically routed outside a building(s) and shall ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 695 Fire Pumps > 695.6 Power Wiring > (A) Supply Conductors > (1) Services and On-Site Power Production Facilities
(7) Special Conditions, On-Site Fuel Supply
Where internal combustion engines are used as the prime mover, an on-site fuel supply shall be provided. The on-site fuel supply shall be secured ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 708 Critical Operations Power Systems (COPS) > 708.20 Sources of Power > (F) Generator Set > (7) On-Site Fuel Supply
705.10 Special Conditions, Identification of Power Sources
or directories for other on-site sources. The plaque or directory shall be marked with the wording "CAUTION: MULTIPLE SOURCES OF POWER." Any posted diagrams shall ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 705 Interconnected Electric Power Production Sources > 705.10 Identification of Power Sources
517.30 Special Occupancies, Sources of Power
of power is supplied by two or more separate central station-fed services experience greater than normal electrical service reliability than those ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.30 Sources of Power
2808.2 Lumber Yards and Woodworking Facilities, Storage Site
Storage sites shall be level and on solid ground or other all-weather surface. Sites shall be thoroughly cleaned before transferring wood products ...
Minnesota Fire Code 2015 > 28 Lumber Yards and Woodworking Facilities > 2808 Storage and Processing of Wood Chips, Hogged Material, Fines, Compost and Raw Product Associated With Yard Waste and Recycling Facilities > 2808.2 Storage Site