(L) 2212 Service Station at a Bulk Plant or Terminal
That portion of a bulk plant property where flammable or combustible liquids are stored and dispensed from fixed equipment into the fuel tanks of motor vehicles, marine craft or approved containers shall comply with this paragraph and NFPA 30A as listed in rule 1301:7-7-47 of the Administrative Code.
Motor fuel-dispensing facility operations shall be totally independent of the bulk plant operations to include:
(a) Above-ground tanks located in the bulk plant shall not supply dispensing devices at the motor fuel-dispensing facility.
(b) Storage tanks at the motor fuel-dispensing facility shall not be connected by piping to aboveground tanks located in the bulk plant.
Effective Date: November 1, 2011
Prior Effective Dates: 1/1/77; 7/1/79; 12/10/82; 7/1/83; 6/1/85; 5/9/88; 11/5/90; 6/28/92; 9/1/95; 1/9/98; 1/3/00; 9/1/05; 7/1/07