// CODE SNIPPET
230.28 Service Masts as Supports
JUMP TO FULL CODE CHAPTER
The service mast shall be of adequate strength or be supported by braces or guy wires to withstand safely the strain imposed by the service-drop or overhead service conductors. Hubs intended for use with a conduit that serves as a service mast shall be identified for use with service-entrance equipment.
Service-drop or overhead service conductors shall not be attached to a service mast between a weatherhead or the end of the conduit and a coupling, where the coupling is located above the last point of securement to the building or other structure or is located above the building or other structure.
Related Code Sections
230.28 Wiring and Protection, Service Masts as Supports
Only power service-drop or overhead service conductors shall be permitted to be attached to a service mast. Service masts used for the support ...
National Electrical Code 2020 of Texas > 2 Wiring and Protection > 230 Services > 230.28 Service Masts as Supports
810.12 Communications Systems, Supports
Outdoor antennas and lead-in conductors shall be securely supported. The antennas or lead-in conductors shall not be attached to the electric service ...
National Electrical Code 2020 of Texas > 8 Communications Systems > 810 Radio and Television Equipment > 810.12 Supports
225.17 Wiring and Protection, Masts as Supports
Masts used for the support of final spans of feeders or branch circuits shall be installed in accordance with 225.17(A) and (B ...
National Electrical Code 2020 of Texas > 2 Wiring and Protection > 225 Outside Branch Circuits and Feeders > 225.17 Masts as Supports
342.30 Wiring Methods and Materials, Securing and Supporting
IMC shall be installed as a complete system in accordance with 300.18 and shall be securely fastened in place and supported in accordance with 342.30 ...
National Electrical Code 2020 of Texas > 3 Wiring Methods and Materials > 342 Intermediate Metal Conduit: Type IMC > 342.30 Securing and Supporting