// CODE SNIPPET
E 503.5.1.5 Sensor Accuracy
JUMP TO FULL CODE CHAPTER
Outdoor air, return air, mixed air, and supply air sensors shall be calibrated within the following accuracies:
- Dry-bulb and wet-bulb temperatures shall be accurate to ±2°F (1.1°C) over the range of 40°F (4.4°C) to 80°F (27°C).
- Enthalpy and the value of a differential enthalpy sensor shall be accurate to ±3 Btu/lb (7 E+03 J/kg) over the range of 20 Btu/lb (4.6 E+04 J/kg) to 36 Btu/lb (8.4 E+04 J/kg).
- Relative humidity shall be accurate to ±5 percent over the range of 20 percent to 80 percent relative humidity. [ASHRAE 90.1:184.108.40.206.6]