This section determines what technical approach is to be used for the seismic evaluation and design for existing buildings. For those buildings or portions of buildings for which Section 317 requires action, the procedures and limitations for the evaluation of existing buildings and design of retrofit systems and/or repair thereof shall be implemented in accordance with this section.
One of the following approaches must be used:
- Method A of Section 320;
- Method B of Section 321, with independent review of a peer reviewer as required in Section 322; or
- For state-owned buildings only, the use of one of the specific procedures listed in Section 319.1.1.
When Method B is chosen it must be approved by the building official, and, where applicable, by the peer reviewer. All referenced standards in ASCE 41 shall be replaced by referenced standards listed in Chapter 35 of the California Building Code.
- [BSC] For buildings constructed to the requirements of California Building Code, 2007 or later edition as adopted by the governing jurisdiction, that code is permitted to be used in place of those specified in Section 319.1.
- [DSA-SS & DSA-SS/CC] For public schools and community colleges constructed to the requirements of California Building Code, 2007 or later edition, that code is permitted to be used in place of those specified in Section 319.1 provided the building complies with Seismic Design Category D or higher.
[BSC] For state-owned buildings, the following specific procedures located in Appendix A may be used, without peer review, for their respective types of construction to comply with the seismic performance requirements for Risk Category I, II or III buildings:
- Seismic Strengthening Provisions for Unreinforced Masonry Bearing Wall Buildings (Chapter A1).
- Prescriptive Provisions for Seismic Strengthening of Cripple Walls and Sill Plate Anchorage of Light Wood-Frame, Residential Buildings (Chapter A3).
- Earthquake Hazard Reduction in Existing Reinforced Concrete and Reinforced Masonry Wall Buildings with Flexible Diaphragms (Chapter A2).
When a design project is begun under Method B the selection of the peer reviewer is subject to the approval of the building official. Following approval by the peer reviewer, the seismic criteria for the project and the planned evaluation provisions must be approved by the building official. The approved seismic criteria and evaluation provisions shall apply. Upon approval of the building official these are permitted to be modified.
For state-owned and community college buildings, where unreinforced masonry is not bearing, it may be used only to resist applied lateral loads. Where unrein-forced masonry walls are part of the structure they must be assessed for stability under the applicable nonstructural evaluation procedure.
[DSA-SS, DSA-SS/CC]For public schools, unreinforced masonry shall not be used to resist in-plane or out-of-plane seismic forces or superimposed gravity loads.
For public schools of light-frame construction, horizontal diaphragms and vertical shear walls shall consist of either diagonal lumber sheathing or structural panel sheathing. Braced horizontal diaphragms may be acceptable when approved by DSA. Straight lumber sheathing may be used in combination with diagonal or structural panel sheathing as diaphragms or shear walls. Let-in bracing, plaster (stucco), hollow clay tile, gypsum wallboard and particle-board sheathing shall not be assumed to resist seismic forces.
The existing condition and properties of the entire structure must be determined and documented by thorough inspection of the structure and site, review of all available related construction documents, review of geotechnical and engineering geologic reports, and performance of necessary testing and investigation. Where samples from the existing structure are taken or in situ tests are performed, they shall be selected and interpreted in a statistically appropriate manner to ensure that the properties determined and used in the evaluation or design are representative of the conditions and structural circumstances likely to be encountered in the structure as a whole. Adjacent structures or site features that may affect the retrofit design shall be identified.
The entire load path of the seismic-force-resisting system shall be determined, documented and evaluated. The load path includes all the horizontal and vertical elements participating in the structural response: such as diaphragms, diaphragm chords, diaphragm collectors, vertical elements such as walls frames, braces; foundations and the connections between the components and elements of the load path. Repaired or retrofitted elements and the standards under which the work was constructed shall be identified.
Data collection in accordance with ASCE 41 Section 6.2 shall meet the following minimum levels:
- [BSC] For state-owned buildings, the requirements shall be met following the data collection requirements of ASCE 41, Section 6.2.
- [DSA-SS, DSA-SS/CC] For public schools and community college buildings constructed in conformance with the Field Act, the “Usual” level as defined in ASCE 41, Section 6.2.2.
- [DSA-SS, DSA-SS/CC] For public schools and community college buildings not constructed in conformance with the Field Act, the “Comprehensive” level as defined in ASCE 41, Section 6.2.3.
Concrete material requirements and testing for public school and community college buildings shall also comply with Sections 1911A and 1909.5 of the California Building Code, respectively.
Qualified test data from the original construction may be accepted, in part or in whole, by the enforcement agency to fulfill the data collection requirements.
- The number of samples for data collection may be adjusted with approval of the enforcement agency when it has been determined that adequate information has been obtained or additional information is required.
- Welded steel moment frame connections of buildings that may have experienced potentially damaging ground motions shall be inspected in accordance with Chapters 3 and 4, FEMA 352, Recommended Post Earthquake Evaluation and Repair Criteria for Welded Moment-Frame Construction for Seismic Applications (July 2000).
Where original building plans and specifications are not available, “as-built” plans shall be prepared that depict the existing vertical and lateral structural systems, exterior elements, foundations and nonstructural systems in sufficient detail to complete the design.
Data collection shall be directed and observed by the project structural engineer or design professional in charge of the design.
Soil profile shall be assigned in accordance with the requirements of Chapter 18 of the California Building Code.
For purposes of earthquake-resistant design, each structure shall be placed in one of the risk categories in accordance with the requirements of the California Building Code.
Each structure shall be designated structurally regular or irregular in accordance with the requirements of ASCE 41, Sections 126.96.36.199.1 to 188.8.131.52.4.
The requirements of Method B (Section 321) may be used for any existing building.
When the building contains prestressed or posttensioned structural components (beams, columns, walls or slabs) or contains precast structural components (beams, columns, walls or flooring systems).
When the building is classified as irregular in vertical or horizontal plan by application of ASCE 7, Section 12.3 and/or ASCE 41, Sections 184.108.40.206.1 to 220.127.116.11.4, unless the irregularity is demonstrated not to affect the seismic performance of the building.
Exception: If the retrofit design removes the configurational attributes that caused the building to be classified as irregular, then Section 319.7.2 does not apply and Method A may be used.
For any building that is assigned to Risk Category IV.
For any building using undefined or hybrid structural systems.
When seismic isolation or energy dissipation systems are used in the retrofit or repair, either as part of the existing structure or as part of the modifications.
When the height of the structure exceeds 240 feet (73 152 mm).
When ASCE 41 is the evaluation standard and its application requires the use of nonlinear procedures.
All components of the lateral-force-resisting system must have the strength to meet the acceptance criteria prescribed in ASCE 41, Chapter 7 or as prescribed in the applicable Appendix A chapter of this code if a specific procedure in Section 319.1.1 is used. Any component not having this strength shall have its capacity increased by modifying or supplementing its strength so that it exceeds the demand, or the demand is reduced to less than the existing strength by making other modifications to the structural system.
Exception: A component’s strength is permitted to be less than that required by the specified seismic load combinations if it can be demonstrated that the associated reduction in seismic performance of the component or its removal due to the failure does not result in a structural system that does not comply with the required performance objectives of Section 317. If this exception is taken for a component, then it cannot be considered part of the primary lateral-load-resisting system.
Where the nonstructural performance levels required by Section 317, Table 317.5 are N-C or higher, mechanical, electrical and plumbing components shall comply with the provisions of ASCE 41, Chapter 13, Section 13.2.
Exception: Modifications to the procedures and criteria may be made subject to approval by the building official, and concurrence of the peer reviewer if applicable. All reports and correspondence shall also be forwarded to the building official.
Structural, geotechnical and construction observation, testing and inspection as used in this section shall mean meeting the requirements of Chapter 17 of the California Building Code, with a minimum allowable level of investigation corresponding to seismic design category (SDC) D. At a minimum the project site will be visited by the responsible design professional to observe existing conditions and to review the construction work for general compliance with approved plans, specifications and applicable structural regulations. Such visits shall occur at significant construction stages and at the completion of the structural retrofit. Structural observation shall be provided for all structures. The plan for testing and inspection shall be submitted to the building official for review and approval with the application for permit.
Additional requirements: For public schools and community colleges, construction material testing, inspection and observation during construction shall also comply with Section 4-333 of the California Administrative Code.
The registered design professional, or their designee, responsible for the structural design shall be retained to perform structural observation and independently report to the owner of observations and findings as they relate to adherence to the permitted plans and good workmanship.
At the conclusion of construction, the structural observer shall submit to the enforcement agency and the owner a final written statement that the required site visits have been made, that the work, to the best of the structural observers knowledge and belief, is or is not in general conformity to the approved plans and that the observed structural deficiencies have been resolved and/or listing those that, to the best of the structural observers knowledge and belief, have not been satisfactorily corrected.
The requirement for structural observation shall be noted and prominently displayed on the front sheet of the approved plans and incorporated into the general notes on the approved plans.
A preconstruction meeting is mandatory for all projects which require structural observation. The meeting shall include, but is not limited to, the registered design professional, structural observer, general constructor, affected subcontractors, the project inspector and a representative of the enforcement agency (designated alternates may attend if approved by the structural observer). The structural observer shall schedule and coordinate this meeting. The purpose of the meeting is to identify and clarify all essential structural components and connections that affect the lateral and vertical load systems and to review scheduling of the required observations for the project’s structural system retrofit.
When compatible with the building use, and the time phasing for both use and the retrofit program, temporary shoring or other structural support is permitted to be considered. Temporary bracing, shoring and prevention of falling hazards are permitted to be used to qualify for Exception 1 in Section 319.12 that allows inadequate capability in some existing components, as long as the required performance levels given in Section 317 can be provided by the permanent structure. The consideration for such temporary actions shall be noted in the design documents.
Where modifications of existing structural components and additions of new structural components are initiated for the purpose of improving the lateral-force resisting strength or stiffness of an existing structure and they are not required by other sections of this code, then they are permitted to be designed to meet an approved seismic performance criteria provided that an engineering analysis is submitted that follows:
- The capacity of existing structural components required to resist forces is not reduced, unless it can be demonstrated that reduced capacity meets the requirements of Section 319.8.
- The lateral loading to or strength requirement of existing structural components is not increased beyond their capacity.
- New structural components are detailed and connected to the existing structural components as required by the California Building Code.
- New or relocated nonstructural components are detailed and connected to existing or new structural components as required by the California Building Code.
- A dangerous condition is not created.
Use of ASCE 41 Tier 1 and Tier 2 deficiency only retrofit procedures are pre-approved for use where Section 317.3 does not require an assessment.
[BSC] Voluntary modifications to lateral force-resisting systems conducted in accordance with Appendix A of this code and the referenced standards of the California Building Code shall be permitted.
[BSC]When Section 319.12 is the basis for structural modifications, the approved design documents must clearly state the scope of the seismic modifications and the accepted criteria for the design. The approved design documents must clearly have the phrase “The seismic requirements of the California Existing Building Code have not been checked to determine if these structural modifications meet the full seismic evaluation and strengthening requirements of Sections 317-322: the modifications proposed are to a different seismic performance standard than would be required in Section 319 if they were not voluntary as allowed in Section 319.12.”