// CODE SNIPPET
402.6.3 Securing Floor-Mounted, Back-Outlet Water Closet Bowls
Go To Full Code Chapter
Floor-mounted, back-outlet water closet bowls shall be set level with an angle of 90 degrees (1.57 rad) between the floor and wall at the centerline of the fixture outlet. The floor and wall shall have a flat mounting surface not less than 5 inches (127 mm) to the right and left of the fixture outlet centerline. The fixture shall be secured to the wall outlet flange or drainage connection and the floor by corrosion-resistant screws or bolts. The closet flange shall be secured to a firm base.
Where floor-mounted, back-outlet water closets are used, the soil pipe shall be not less than 3 inches (80 mm) in diameter. Offset, eccentric, or reducing closet flanges shall not be used.
Related Code Sections
402.6.3 Plumbing Fixtures and Fixture Fittings, Securing Floor-Mounted, Back-Outlet Water Closet Bowls
Floor-mounted, back-outlet water closet bowls shall be set level with an angle of 90 degrees (1.57 rad) between the floor and wall at the centerline ...
405.1 Plumbing Fixtures and Fixture Fittings, Prohibited Water Closets
A water closet that might permit siphonage of the contents of the bowl back into the tank shall be prohibited ...
Section P2712 Plumbing Fixtures, Water Closets
and unventilated space or walls that are not thoroughly washed at each discharge shall be prohibited. Water closets that allow backflow of the contents of the bowl ...
E 501.3 Manufactured/Mobile Home Parks and Recreational Vehicle Parks, Water Closets
Water closets shall be of an approved, elongated bowl type and shall be provided with seats with open fronts ...
411.0 Plumbing Fixtures and Fixture Fittings, Water Closets
Water closets shall comply with ASME A112.19.2/CSA B45.1, ASME A112.19.3/CSA B45.4, or CSA B45.5/IAPMO Z124. Water closet bowls for public use shall ...