// CODE SNIPPET
(2) Same Vertical Section
JUMP TO FULL CODE CHAPTER
Other than the required interconnections and control wiring, only those conductors that are intended for termination in a vertical section of a switchboard or switchgear shall be located in that section.
Related Code Sections
(2) Equipment for General Use, Same Vertical Section
Other than the required interconnections and control wiring, only those conductors that are intended for termination in a vertical section ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 408 Switchboards, Switchgear, and Panelboards > 408.3 Support and Arrangement of Busbars and Conductors > (A) Conductors and Busbars on a Switchboard, Switchgear, or Panelboard > (2) Same Vertical Section
(G) Special Conditions, Connection Ahead of Service Disconnecting Means
Where approved by the authority having jurisdiction, connections located ahead of and not within the same cabinet, enclosure, vertical switchgear ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 701 Legally Required Standby Systems > 701.12 General Requirements > (G) Connection Ahead of Service Disconnecting Means
(1) Special Equipment, Electric Utility Service Connection
, vertical switchgear section, or vertical switchboard section as the service disconnecting means. The connection shall be located and arranged so ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 695 Fire Pumps > 695.3 Power Source(s) for Electric Motor-Driven Fire Pumps > (A) Individual Sources > (1) Electric Utility Service Connection
(B) Special Conditions, Wiring
)(b). Emergency circuits shall not originate from the same vertical switchgear section, vertical switchboard section, panelboard enclosure ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 700 Emergency Systems > 700.10 Wiring, Emergency System > (B) Wiring
R608.7.2.2.3 Wall Construction, Vertical Shear Reinforcement
are used, solid wall segments shall have vertical reinforcement consisting of minimum No. 4 bars. Vertical shear reinforcement shall be the same grade ...
2020 Minnesota Residential Code > 6 Wall Construction > R608 Exterior Concrete Wall Construction > R608.7 Solid Walls for Resistance to Lateral Forces > R608.7.2 Solid Wall Segments > R608.7.2.2 Reinforcement in Solid Wall Segments > R608.7.2.2.3 Vertical Shear Reinforcement