// CODE SNIPPET
Section 21.1306 — Residue, Popping and Pitting
JUMP TO FULL CODE CHAPTER
The four types of hydrated lime for masonry purposes shall conform to one of the following requirements:
- The residue retained on a No. 30 (600 μm) sieve shall not be more than 0.5 percent, or
- If the residue retained on a No. 30 (600 μm) sieve is over 0.5 percent, the lime shall show no pops and pits when tested.
Related Code Sections
Section 21.1306 Referenced Standards, — Residue, Popping and Pitting
) sieve shall not be more than 0.5 percent, or If the residue retained on a No. 30 (600 μm) sieve is over 0.5 percent, the lime shall show no pops ...
Los Angeles Existing Building Code > Referenced Standards > 21-13 Hydrated Lime for Masonry Purposes > 21.1306 — Residue, Popping and Pitting
2403.4.2 Flammable Finishes, Residue
Residues removed during cleaning and debris contaminated with residue shall be immediately removed from the premises and properly disposed ...
2017 LA City Fire Code > 24 Flammable Finishes > 2403 Protection of Operations > 2403.4 Operations and Maintenance > 2403.4.2 Residue
184.108.40.206* Design Approaches, Residual Pressure
The residual pressure requirement of Table 220.127.116.11 shall be met at the elevation of the highest sprinkler ...
Standard for the Installation of Sprinkler Systems 2016 of Los Angeles > 11 Design Approaches > 11.2 Occupancy Hazard Fire Control Approach for Spray Sprinklers > 11.2.2 Water Demand Requirements — Pipe Schedule Method > 18.104.22.168* Residual Pressure
2408.4.3 Flammable Finishes, Residue Control
Materials shall not be contaminated by dusts and overspray residues resulting from the sanding or spraying of finishing materials containing organic ...
2017 LA City Fire Code > 24 Flammable Finishes > 2408 Organic Peroxides and Dual-Component Coatings > 2408.4 Housekeeping, Maintenance, Storage and Use of Hazardous Materials > 2408.4.3 Residue Control
22.214.171.124.1 Definitions, Residual Pressure.
The pressure that exists in the distribution system, measured at the residual hydrant at the time the flow readings are taken at the flow hydrants ...
Standard for the Installation of Sprinkler Systems 2016 of Los Angeles > 3 Definitions > 3.8 Private Water Supply Piping Definitions > 3.8.1 General Definitions From NFPA 24 > 126.96.36.199 Pressure. > 188.8.131.52.1 Residual Pressure.