// CODE SNIPPET
2113.11.1 Residential-Type Appliances and Low Heat Appliances (General)
JUMP TO FULL CODE CHAPTER
Flue lining systems shall comply with one of the following:
- Clay flue lining complying with the requirements of ASTM C 315.
- Listed chimney lining systems complying with UL 1777.
- Factory-built chimneys or chimney units listed for installation within masonry chimneys.
- Other approved materials that will resist corrosion, erosion, softening or cracking from flue gases and condensate at temperatures up to 1,800°F (982°C).
Pellet fuel-burning appliances may be installed only when their use is permitted by the New York City Air Pollution Control Code. Any such appliances shall be listed and labeled and shall be installed in accordance with the terms of the listing. If permitted, such appliances shall be operated in compliance with the New York City Air Pollution Control Code. Flue lining and vent systems for use in masonry chimneys with pellet fuel-burning appliances shall be limited to flue lining systems complying with Section 2113.11.1 and pellet vents listed for installation within masonry chimneys (see Section 218.104.22.168 for marking).
When a flue is relined with a material not complying with Section 2113.11.1, the chimney shall be plainly and permanently identified by a label attached to a wall, ceiling or other conspicuous location adjacent to where the connector enters the chimney. The label shall include the following message or equivalent language: "This chimney is for use only with (type or category of appliance) that burns (type of fuel). Do not connect other types of appliances."