// CODE SNIPPET
312.1 Required Tests and Inspections
JUMP TO FULL CODE CHAPTER
The permit holder shall make the applicable tests prescribed in Sections 312.2 through 312.9 to determine compliance with the provisions of this code. The permit holder shall give reasonable advance notice to the code official when the plumbing work is ready for tests. The equipment, material, power and labor necessary for the inspection and test shall be furnished by the permit holder and the permit holder shall be responsible for determining that the work will withstand the test pressure prescribed in the following tests. All plumbing system piping shall be tested with either water or by air. Plumbing system pipe shall be tested in accordance with the manufacturer's installation instructions. After the plumbing fixtures have been set and their traps filled with water, the entire drainage system shall be submitted to final tests. The code official shall require the removal of any cleanouts if necessary to ascertain whether the pressure has reached all parts of the system.
Gauges used for testing shall be as follows:
- Tests requiring a pressure of 10 pounds per square inch (psi) (69 kPa) or less shall utilize a testing gauge having increments of 0.10 psi (0.69 kPa) or less.
- Tests requiring a pressure of greater than 10 psi (69 kPa) but less than or equal to 100 psi (689 kPa) shall utilize a testing gauge having increments of 1 psi (6.9 kPa) or less.
- Tests requiring a pressure of greater than 100 psi (689 kPa) shall utilize a testing gauge having increments of 2 psi (14 kPa) or less.
The holder of the permit shall be responsible for the scheduling of the following inspections:
- Underground inspection shall be made after trenches or ditches are excavated and bedded, piping installed, and before any backfill is put in place.
- Rough-in inspection shall be made of completed portions of all sanitary, storm and water distribution piping, after the framing, fireblocking, firestopping, draft-stopping and bracing for that portion is in place, and prior to the installation of wall or ceiling membranes.
- Final inspection shall be made after the building is complete, all plumbing fixtures are in place and properly connected, and the structure is ready for occupancy.