// CODE SNIPPET
110.3 Required Progress Inspections
JUMP TO FULL CODE CHAPTER
Footing and foundation inspections shall be made after excavations for footings are complete and any required reinforcing steel is in place. For concrete foundations, any required forms shall be in place prior to inspection. Materials for the foundation shall be on the job, except where concrete is ready mixed in accordance with ASTM C 94, the concrete need not be on the job.
Fire-resistance-rated construction shall be inspected to determine compliance with the approved construction documents, including inspection of the following work: wall assembly is limited to through-penetration firestopping and, in the course of work, the cutting away or removal of any part of the existing fire-resistance-rated construction becomes necessary in the general area surrounding the penetration, not to exceed 4 square feet (0.37 m2) in any given area, the progress inspection for fire-resistance-rated construction shall not be required provided that the special inspection agency for the through-penetration firestopping special inspection verifies that the removed portion of fire-resistance-rated construction (i) is less than 4 square feet (0.37 m2), and (ii) has been restored to its original condition.
Related Code Sections
109.3 Administration, Required Progress Inspections
The inspections set forth in Sections 109.3.1 through 109.3.8 shall be made during the progress of work to verify substantial compliance ...
110.3 Administration, Required Progress Inspections
the penetration, not to exceed 4 square feet (0.37 m 2 ) in any given area, the progress inspection for fire-resistance-rated construction shall not be required ...
109.3.2 Administration, Lowest Floor Elevation
construction, the elevation inspection report required in Item 1 of Section G105.3 of Appendix G shall be submitted to the department ...
NYC Building Code 2008 > 1 Administration > 109 Inspections > 109.3 Required Progress Inspections > 109.3.2 Lowest Floor Elevation
109.3.4 Administration, Fire-Resistance Rated Construction Inspection
Fire resistance rated construction shall be inspected to determine compliance with the approved construction documents, including inspection ...
NYC Building Code 2008 > 1 Administration > 109 Inspections > 109.3 Required Progress Inspections > 109.3.4 Fire-Resistance Rated Construction Inspection