// CODE SNIPPET
23-21 Required Floor Area Per Dwelling Unit
Go To Full Code Chapter
R1 R2 R3 R4 R5 R6 R7 R8 R9 R10
This Section shall apply to existing buildings in which the number of dwelling units is increased as well as to all new development.
Any given floor area shall be counted only once in meeting the floor area requirements.
In all districts, as indicated, the floor area requirement per dwelling unit shall not be less than as set forth in this Section, except as provided in Sections 23-24 (Special Provisions for Buildings Containing Multiple Uses) or Section 23-25 (Special Provisions for Existing Small Zoning Lots).
Related Code Sections
29.5 Single- And Multiple-Station Alarms and Household Fire Alarm Systems, Detection and Notification
of a dwelling unit, excluding garage areas, is greater than 1000 ft2 (93 m2), smoke alarms shall be installed per 188.8.131.52.1 and 184.108.40.206.2 ...
908.7.1.1 Fire Protection Systems, Affected Dwelling Units
Carbon monoxide alarms or detectors shall be required within the following dwelling units: Units on the same story where carbon monoxide- producing ...
§27-758 Light, Heat, Ventilation and Noise Control, Kitchens
Kitchens shall be ventilated as follows: (a) Kitchens located within dwelling units and having a floor area of greater than fifty-nine square feet ...
908.7.1 Fire Protection Systems, Group I-1 and R Occupancies
notification appliances shall be installed in affected dwelling units as per Section 908.7.1.1 and shall be annunciated by dwelling unit at a constantly ...
Reference Standard 16 Plumbing and Gas Piping [PDF] (page 24)
but for not more than 1/2 of Over 300 pupils of the largest class using at least 1 the required number of water 1/100 pupils pool at any one time per floor ...