// CODE SNIPPET
407.3.3 Reopening Device
JUMP TO FULL CODE CHAPTER
Elevator doors shall be provided with a reopening device complying with 407.3.3 that shall stop and reopen a car door and hoistway door automatically if the door becomes obstructed by an object or person.
EXCEPTION: Existing elevators with manually operated doors shall not be required to comply with 407.3.3.
The device shall be activated by sensing an obstruction passing through the opening at 5 inches (125 mm) nominal and 29 inches (735 mm) nominal above the finish floor.
The device shall not require physical contact to be activated, although contact is permitted to occur before the door reverses.
Door reopening devices shall remain effective for 20 seconds minimum.
Related Code Sections
407.3.3 Accessible Routes, Reopening Device
Elevator doors shall be provided with a reopening device complying with 407.3.3 that shall stop and reopen a car door and hoistway door automatically ...
Texas Accessibility Standards 2012 > 4 Accessible Routes > 407 Elevators > 407.3 Elevator Door Requirements > 407.3.3 Reopening Device
416.3 Gas Piping Installations, Devices
Pressure-relieving or pressure-limiting devices shall be one of the following: Pressure relief valve. Monitoring regulator. Series regulator ...
Fuel Gas Code of the Texas Industrialized Housing and Buildings Program > 4 Gas Piping Installations > 416 (IFGS) Overpressure Protection Devices > 416.3 Devices
106.5.70 Application and Administration, Transfer Device
Equipment designed to facilitate the transfer of a person from a wheelchair or other mobility aid to and from an amusement ride seat ...
Texas Accessibility Standards 2012 > 1 Application and Administration > 106 Definitions > 106.5 Defined Terms > 106.5.70 Transfer Device
1110.2 Storm Drainage, Control Devices
The control devices shall be installed so that the rate of discharge of water per minute shall not exceed the values for continuous flow as indicated ...
Plumbing Code of the Texas Industrialized Housing and Buildings Program > 11 Storm Drainage > 1110 Controlled Flow Roof Drain Systems > 1110.2 Control Devices
1306.4 Fuel Oil Piping and Storage, Gauging Devices
Gauging devices such as liquid level indicators or signals shall be designed and installed so that oil vapor will not be discharged into a building ...
Mechanical Code of the Texas Industrialized Housing and Buildings Program > 13 Fuel Oil Piping and Storage > 1306 Oil Gauging > 1306.4 Gauging Devices