// CODE SNIPPET
902.1.1 Recirculating Air or Exhaust Systems
JUMP TO FULL CODE CHAPTER
Where a floor is served by a recirculating air or exhaust system with a capacity greater than 15,000 cubic feet per minute (701 m3/s), that system shall be equipped with approved smoke and heat detection devices installed in accordance with the International Mechanical Code.
Related Code Sections
902.1.1 Alterations—Level 3, Recirculating Air or Exhaust Systems
Where a floor is served by a recirculating air or exhaust system with a capacity greater than 15,000 cubic feet per minute (701 m 3 /s), that system ...
2018 Philadelphia Existing Building Code > 9 Alterations—Level 3 > 902 Special Use and Occupancy > 902.1 High-Rise Buildings > 902.1.1 Recirculating Air or Exhaust Systems
409.3.2 Special Detailed Requirements Based on Occupancy and Use, Exhaust Air
in such a location that the exhaust air cannot be readily recirculated into any air supply system. The projection room ventilation system is permitted ...
2018 Philadelphia Building Code > 4 Special Detailed Requirements Based on Occupancy and Use > 409 Motion Picture Projection Rooms > 409.3 Projection Room and Equipment Ventilation > 409.3.2 Exhaust Air
403.2 Ventilation, Outdoor Air Required
of the resulting supply airstream consists of air recirculated from these spaces. Where mechanical exhaust is required by Note b in Table 403.3.1.1, recirculation ...
2018 Philadelphia Mechanical Code > 4 Ventilation > 403 Mechanical Ventilation > 403.2 Outdoor Air Required
Section 403 Light, Ventilation and Occupancy Limitations, Ventilation
with a mechanical ventilation system. Air exhausted by a mechanical ventilation system from a bathroom or toilet room shall discharge ...
Philadelphia Property Maintenance Code > 4 Light, Ventilation and Occupancy Limitations > 403 Ventilation