// CODE SNIPPET
(E) Receptacles in Countertops
JUMP TO FULL CODE CHAPTER
Receptacle assemblies for installation in countertop surfaces shall be listed for counter-top applications. Where receptacle assemblies for countertop applications are required to provide ground-fault circuit-interrupter protection for personnel in accordance with 210.8, such assemblies shall be permitted to be listed as GFCI receptacle assemblies for countertop applications.
Related Code Sections
(E) Equipment for General Use, Receptacles in Countertops
Receptacle assemblies for installation in countertop surfaces shall be listed for counter-top applications. Where receptacle assemblies ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 406 Receptacles, Cord Connectors, and Attachment Plugs (Caps) > 406.5 Receptacle Mounting > (E) Receptacles in Countertops
(3) Wiring and Protection, Receptacle Outlet Location
Receptacle outlets shall be located in one or more of the following: On or above countertop or work surfaces: On or above, but not more than 500 ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 210 Branch Circuits > 210.52 Dwelling Unit Receptacle Outlets > (C) Countertops and Work Surfaces > (3) Receptacle Outlet Location