// CODE SNIPPET
625.56 Receptacle Enclosures
JUMP TO FULL CODE CHAPTER
All receptacles installed in a wet location for electric vehicle charging shall have an enclosure that is weatherproof with the attachment plug cap inserted or removed. An outlet box hood installed for this purpose shall be listed and shall be identified as extra duty. Other listed products, enclosures, or assemblies providing weatherproof protection that do not utilize an outlet box hood shall not be required to be marked extra duty.
Related Code Sections
625.56 Special Equipment, Receptacle Enclosures
All receptacles installed in a wet location for electric vehicle charging shall have an enclosure that is weatherproof with the attachment plug cap ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 625 Electric Vehicle Power Transfer System > 625.56 Receptacle Enclosures
(1) Equipment for General Use, Grounding-Type Receptacles
Where a grounding means exists in the receptacle enclosure or an equipment grounding conductor is installed in accordance with 250.130(C), grounding ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 406 Receptacles, Cord Connectors, and Attachment Plugs (Caps) > 406.4 General Installation Requirements > (D) Replacements > (1) Grounding-Type Receptacles
545.10 Special Occupancies, Receptacle or Switch With Integral Enclosure
A receptacle or switch with integral enclosure and mounting means, where tested, identified, and listed to applicable standards, shall be permitted ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 545 Manufactured Buildings and Relocatable Structures > 545.10 Receptacle or Switch With Integral Enclosure
(C) Special Equipment, Receptacle, Maximum
receptacles. For purposes of this requirement, a receptacle is considered (1) up to two (simplex) receptacles provided within a single enclosure ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 605 Office Furnishings > 605.9 Freestanding-Type Office Furnishings, Cord-And Plug-Connected > (C) Receptacle, Maximum