// CODE SNIPPET
1003.3.5.2 Rate of Flow Controls
JUMP TO FULL CODE CHAPTER
Grease interceptors shall be equipped with devices to control the rate of water flow so that the water flow does not exceed the rated flow. The flow-control device shall be vented and terminate not less than 6 inches (152 mm) above the flood rim level or be installed in accordance with the manufacturer's instructions.