// CODE SNIPPET
Section M1503 Range Hoods
JUMP TO FULL CODE CHAPTER
Range hoods shall discharge to the outdoors through a duct. The duct serving the hood shall have a smooth interior surface, shall be air tight, shall be equipped with a back-draft damper and shall be independent of all other exhaust systems. Ducts serving range hoods shall not terminate in an attic or crawl space or areas inside the building.
Ducts serving range hoods shall be constructed of galvanized steel, stainless steel or copper.
Exception: Ducts for domestic kitchen cooking appliances equipped with down-draft exhaust systems shall be permitted to be constructed of schedule 40 PVC pipe and fittings provided that the installation complies with all of the following:
- The duct is installed under a concrete slab poured on grade.
- The underfloor trench in which the duct is installed is completely backfilled with sand or gravel.
- The PVC duct extends not more than 1 inch (25 mm) above the indoor concrete floor surface.
- The PVC duct extends not more than 1 inch (25 mm) above grade outside of the building.
- The PVC ducts are solvent cemented.
Exhaust hood systems capable of exhausting in excess of 400 cubic feet per minute (0.19 m3/s) shall be mechanically or naturally provided with makeup air at a rate approximately equal to the exhaust air rate. Such makeup air systems shall be equipped with not less than one damper. Each damper shall be a gravity damper or an electrically operated damper that automatically opens when the exhaust system operates. Dampers shall be accessible for inspection, service, repair and replacement without removing permanent construction or any other ducts not connected to the damper being inspected, serviced, repaired or replaced.
Kitchen exhaust makeup air shall be discharged into the same room in which the exhaust system is located or into rooms or duct systems that communicate through one or more permanent openings with the room in which such exhaust system is located. Such permanent openings shall have a net cross-sectional area not less than the required area of the makeup air supply openings.
Related Code Sections
Section M1503 Exhaust Systems, Range Hoods
Range hoods shall discharge to the outdoors through a duct. The duct serving the hood shall have a smooth interior surface, shall be air tight, shall ...
Residential Code for one- and two-family dwellings of the Texas Industrialized Housing and Buildings Program > 15 Exhaust Systems > M1503 Range Hoods
(4) Equipment for General Use, Range Hoods and Microwave Oven/Range Hood Combinations
Range hoods and over-the-range microwave ovens with integral range hoods shall be permitted to be cord-and-plug-connected with a flexible cord ...
National Electrical Code 2020 of Texas > 4 Equipment for General Use > 422 Appliances > 422.16 Flexible Cords > (B) Specific Appliances > (4) Range Hoods and Microwave Oven/Range Hood Combinations
505.4 Exhaust Systems, Other Than Group R
with domestic range hoods. Hoods and exhaust systems shall be in accordance with Sections 505.1 and 505.2 ...
Mechanical Code of the Texas Industrialized Housing and Buildings Program > 5 Exhaust Systems > 505 Domestic Kitchen Exhaust Equipment > 505.4 Other Than Group R
M1901.1 Special Appliances, Equipment and Systems, Clearances
material. Reduced clearances are permitted in accordance with the listing and labeling of the range hoods or appliances . The installation ...
Residential Code for one- and two-family dwellings of the Texas Industrialized Housing and Buildings Program > 19 Special Appliances, Equipment and Systems > M1901 Ranges and Ovens > M1901.1 Clearances