E403.5 Radon Vent Pipe Installation
All portions of the radon vent pipe not permanently encased in a wall or chase shall be labeled to prevent accidental misuse. Labels shall consist of a pressure-sensitive 2-inch (51 mm) yellow band with the words "RADON REDUCTION SYSTEM" printed in black letters at least 1 inch (25 mm) in height. These labels shall be placed on every visible portion of the vent pipe at a spacing of not more than 3 feet (914 mm). The labels shall be placed so as to be visible from any direction.
The size of vent pipes shall be determined by application of appropriate engineering principles, based on air-flow rates predicted with the large-building active soil-depressurization model. For systems that comply with the alternate compliance method, Section E403.2.2, and are installed in buildings with straight runs of vent pipes no more than 50 feet (15 240 mm) in height, the required number and size of vent pipes may be determined as follows:
Radon vent pipes shall terminate with a rain cap, installed above the roof of the structure, and shall be located in accordance with existing codes for toxic or noxious exhausts. If not specifically addressed or applicable, vent pipes shall be terminated in locations that minimize human exposure to their exhaust air, such that the location is:
The total required distance [10 feet (3048 mm)] shall be measured either directly between the two points or be the sum of measurements made around the intervening obstacles. If the discharge point is within two feet of elevation of the opening into conditioned space, the distance [10 feet (3048 mm)] shall be the horizontal distance between the points.