// CODE SNIPPET
12.3.2* Quality Assurance for Penetrations and Joints
JUMP TO FULL CODE CHAPTER
In new buildings three stories or greater in height, a quality assurance program for the installation of devices and systems installed to protect penetration and joints shall be prepared and monitored by the RDP responsible for design. Inspections of firestop systems and fire-resistive joint systems shall be in accordance with 184.108.40.206 and 220.127.116.11.
Inspection of firestop systems of the types tested in accordance with ASTM E814, Standard Test Method for Fire Tests of Through-Penetration Fire Stops, or /UL 1479, Standard for Fire Tests of Through-Penetration Firestops, shall be conducted in accordance with ASTM E2174, Standard Practice for On-Site Inspection of Installed Fire Stops. [5000:40.9.1]
Inspection of fire-resistive joint systems of the types tested in accordance with ASTM E1966, Standard Test Method for Fire-Resistive Joint Systems, or UL 2079, Standard for Tests for Fire Resistance of Buildings Joint Systems, shall be conducted in accordance with ASTM E2393, Standard Practice for On-Site Inspection of Installed Fire Resistive Joint Systems and Perimeter Fire Barriers. [5000:40.9.2]
Related Code Sections
12.3.2* Features of Fire Protection, Quality Assurance for Penetrations and Joints
In new buildings three stories or greater in height, a quality assurance program for the installation of devices and systems installed to protect ...
Fire Code 2018 of West Virginia > 12 Features of Fire Protection > 12.3 Fire-Resistive Materials and Construction > 12.3.2* Quality Assurance for Penetrations and Joints
Section 2105 Masonry, Quality Assurance
A quality assurance program shall be used to ensure that the constructed masonry is in compliance with the approved construction documents . The ...
3.3.222 Definitions, Quality Assurance
The procedures conducted by the registered design professionals (RDPs) responsible for design and the registered design professionals responsible ...
Fire Code 2018 of West Virginia > 3 Definitions > 3.3 General Definitions > 3.3.222 Quality Assurance
118.104.22.168 Hydronic Piping, Full Flow Assurance
Branch tubes shall not restrict the flow in the run tube. A dimple/depth stop shall be formed in the branch tube to ensure that penetration ...
Mechanical Code 2015 of West Virginia > 12 Hydronic Piping > 1203 Joints and Connections > 1203.3 Joint Preparation and Installation > 1203.3.8 Mechanically Formed Tee Fittings > 122.214.171.124 Full Flow Assurance
2211.3.4 Steel, Truss Quality Assurance
Trusses not part of a manufacturing process that provides requirements for quality control done under the supervision of a third-party quality ...
Building Code 2015 of West Virginia > 22 Steel > 2211 Cold-Formed Steel Light-Frame Construction > 2211.3 Truss Design > 2211.3.4 Truss Quality Assurance