Protective environment rooms for the protection of certain immunosuppressed patients may be provided by the facility. Protective environment rooms shall be labeled “Protective Environment Room” on or adjacent to the anteroom side of the door between the isolation room and the anteroom. Protective environment rooms shall contain only one bed.
Protective environment room (s) shall have self-closing and latching devices on all anteroom doors.
A separate anteroom shall be provided between the protective environment room and the corridor, hallway or adjoining space which shall constitute the only entrance to the protective environment room. This anteroom shall have a handwashing fixture, work counter at least 3 feet (914 mm) long, cabinets and space to gown and to store clean and soiled materials. There shall be a view window from the anteroom to the protective environment room. There shall be means to allow for airflow from the protective environment room into the anteroom. Anteroom doors shall be aligned so that large equipment can be wheeled into the protective environment room. One anteroom may serve no more than one protective environment room.
Exception: Alternate designs for protective environment rooms, without individual anterooms, may be approved by the enforcement agency when it can be demonstrated that the alternate design meets the requirements of the California Mechanical Code and does not compromise or alter any health or fire protection component, assembly or system.