// CODE SNIPPET
2705.2.3.2 Protection of Vessels
JUMP TO FULL CODE CHAPTER
- HPM: Vessels containing HPM shall be protected from physical damage and shall not project from the workstation.
- Hazardous cryogenic fluids, gases and liquids: Hazardous cryogenic fluid, gas and liquid vessels located within a workstation shall be protected from seismic forces in an approved manner in accordance with the International Building Code.
- Compressed gases: Protection for compressed gas vessels shall also comply with Section 5303.5.
- Cryogenic fluids: Protection for cryogenic fluid vessels shall also comply with Section 5503.5.
Related Code Sections
2705.2.3.2 Semiconductor Fabrication Facilities, Protection of Vessels
Vessels containing hazardous materials located in or connected to a workstation shall be protected as follows: HPM: Vessels containing HPM shall ...
Fire Code 2018 of Kansas > 27 Semiconductor Fabrication Facilities > 2705 Use and Handling > 2705.2 Fabrication Areas > 2705.2.3 Workstations > 2705.2.3.2 Protection of Vessels
1006.3 Boilers, Water Heaters and Pressure Vessels, Pressure Relief for Pressure Vessels
Pressure vessels shall be protected with a pressure relief valve or pressure-limiting device as required by the manufacturer's installation ...
Mechanical Code 2018 of Kansas > 10 Boilers, Water Heaters and Pressure Vessels > 1006 Safety and Pressure Relief Valves and Controls > 1006.3 Pressure Relief for Pressure Vessels
703.3.4 Gaseous Hydrogen Systems, Vessels Other Than Containers
Vessels other than containers shall be protected with pressure relief devices in accordance with the ASME Boiler and Pressure Vessel Code (Section ...
Fuel Gas Code 2018 of Kansas > 7 Gaseous Hydrogen Systems > 703 (IFGC) General Requirements > 703.3 Pressure Relief Devices > 703.3.4 Vessels Other Than Containers
6003.2.5 Highly Toxic and Toxic Materials, Weather Protection for Highly Toxic Liquids and Solids—Outdoor Storage or Use
903.3.1.1, or storage or use vessels shall be fire resistive. Weather protection shall be provided in accordance with Section 5004.13 for storage ...
Fire Code 2018 of Kansas > 60 Highly Toxic and Toxic Materials > 6003 Highly Toxic and Toxic Solids and Liquids > 6003.2 Outdoor Storage and Use > 6003.2.5 Weather Protection for Highly Toxic Liquids and Solids—Outdoor Storage or Use