// CODE SNIPPET
2404.5.2 Protection of Sprinklers
JUMP TO FULL CODE CHAPTER
Automatic sprinklers installed in flammable vapor areas shall be protected from the accumulation of residue from spraying operations in an approved manner. Bags used as a protective covering shall be 0.003-inch-thick (0.076 mm) polyethylene or cellophane or shall be thin paper. Automatic sprinklers contaminated by overspray particles shall be replaced with new automatic sprinklers.
Related Code Sections
2404.5.2 Flammable Finishes, Protection of Sprinklers
Automatic sprinklers installed in flammable vapor areas shall be protected from the accumulation of residue from spraying operations ...
Fire Code 2018 of Kansas > 24 Flammable Finishes > 2404 Spray Finishing > 2404.5 Housekeeping, Maintenance and Storage of Hazardous Materials > 2404.5.2 Protection of Sprinklers
23.6* Plans and Calculations, Exposure Protection Sprinkler Systems
Exposure protection sprinkler systems shall be hydraulically calculated using Table 23.6.1 based on severity of exposure as indicated by a relative ...
Standard for the Installation of Sprinkler Systems 2016 of Kansas > 23 Plans and Calculations > 23.6* Exposure Protection Sprinkler Systems
8.5.2 Installation Requirements, Protection Areas Per Sprinkler
The protection area of coverage per sprinkler ( A S ) shall be determined as follows: Along branch lines as follows: Determine distance ...
Standard for the Installation of Sprinkler Systems 2016 of Kansas > 8 Installation Requirements > 8.5 Position, Location, Spacing, and Use of Sprinklers > 8.5.2 Protection Areas Per Sprinkler
3504.1.8 Welding and Other Hot Work, Sprinkler Protection
Automatic sprinkler protection shall not be shut off while hot work is performed. Where hot work is performed close to automatic sprinklers ...
Fire Code 2018 of Kansas > 35 Welding and Other Hot Work > 3504 Fire Safety Requirements > 3504.1 Protection of Combustibles > 3504.1.8 Sprinkler Protection
184.108.40.206 System Requirements,
A single line of sprinklers is permitted to protect a maximum of two stories of wall area or two levels of vertically aligned windows where ...
Standard for the Installation of Sprinkler Systems 2016 of Kansas > 7 System Requirements > 7.7 Outside Sprinklers for Protection Against Exposure Fires (Exposure Protection Sprinkler Systems) > 7.7.8 Sprinklers > 220.127.116.11