// CODE SNIPPET
G501.4 Protection of Mechanical Equipment and Outside Appliances
JUMP TO FULL CODE CHAPTER
Mechanical equipment and outside appliances shall be elevated to or above the design flood elevation.
Exception: Where such equipment and appliances are designed and installed to prevent water from entering or accumulating within their components and the systems are constructed to resist hydrostatic and hydrodynamic loads and stresses, including the effects of buoyancy, during the occurrence of flooding up to the elevation required by Section R322 of the International Residential Code, the systems and equipment shall be permitted to be located below the elevation required by Section R322 of the International Residential Code. Electrical wiring systems shall be permitted below the design flood elevation provided they conform to the provisions of NFPA 70.
Related Code Sections
G501.4 Flood-Resistant Construction, Protection of Mechanical Equipment and Outside Appliances
Mechanical equipment and outside appliances shall be elevated to or above the design flood elevation. Exception: Where such equipment ...
2015 Michigan Building Code > G Flood-Resistant Construction > G501 Manufactured Homes > G501.4 Protection of Mechanical Equipment and Outside Appliances
303.4 General Regulations, Protection From Damage
Appliances shall not be installed in a location where subject to mechanical damage unless protected by approved barriers ...
2015 Michigan Mechanical Code > 3 General Regulations > 303 Equipment and Appliance Location > 303.4 Protection From Damage
Article 422 Equipment for General Use, Appliances
Appliances shall be protected against overcurrent in accordance with 422.11(A) through (G ...
907.2.22 Fire Protection Systems, Airport Traffic Control Towers
in all of the following locations: Airport traffic control cab. Electrical and mechanical equipment rooms. Airport terminal radar and electronics ...
2015 Michigan Building Code > 9 Fire Protection Systems > 907 Fire Alarm and Detection Systems > 907.2 Where Required-New Buildings and Structures > 907.2.22 Airport Traffic Control Towers
1205.1.5 Hydronic Piping, Equipment and Appliances
Shutoff valves shall be installed on connections to mechanical equipment and appliances. This requirement does not apply to components ...
2015 Michigan Mechanical Code > 12 Hydronic Piping > 1205 Valves > 1205.1 Where Required > 1205.1.5 Equipment and Appliances