// CODE SNIPPET
[F] 904.13.1 Protection From Fire
JUMP TO FULL CODE CHAPTER
- The automatic fire-extinguishing system shall be of a type recognized for protection of domestic cooking equipment. Preengineered automatic fire-extinguishing systems shall be listed and labeled in accordance with UL 300A and installed in accordance with the manufacturer's instructions.
- Manual actuation of the fire-extinguishing system shall be provided in accordance with Section 904.12.1.
- Interconnection of the fuel and electric power supply shall be in accordance with Section 904.12.2.
Cooktops and ranges shall include burners that have been tested and listed to prevent ignition of cooking oil with burners turned on to their maximum heat settings and allowed to operate for 30 minutes.
Related Code Sections
904.13.1 Fire Protection and Life Safety Systems, Protection From Fire
recognized for protection of domestic cooking equipment. Preengineered automatic fire-extinguishing systems shall be listed and labeled in accordance ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 904 Alternative Automatic Fire-Extinguishing Systems > 904.13 Domestic Cooking Systems > 904.13.1 Protection From Fire
4184.108.40.206 Special Detailed Requirements Based on Occupancy and Use, Tank Protection
Storage tanks shall be noncombustible and protected from physical damage. Fire barriers or horizontal assemblies or both around the storage tanks ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.9 Group H-2 > 415.9.1 Flammable and Combustible Liquids > 4220.127.116.11 Tank Protection
(2) Special Equipment, Feeders
with the fire pump system. (c) Protection from Potential Damage. The conductors shall be protected from potential damage by fire, structural failure ...
National Electrical Code 2017 of Illinois > 6 Special Equipment > 695 Fire Pumps > 695.6 Power Wiring > (A) Supply Conductors > (2) Feeders
907.4.2.5 Fire Protection and Life Safety Systems, Protective Covers
alarms or to provide the manual fire alarm box with protection from physical damage. The protective cover shall be transparent or red in color ...
Building Code 2018 of Illinois > 9 Fire Protection and Life Safety Systems > 907 Fire Alarm and Detection Systems > 907.4 Initiating Devices > 907.4.2 Manual Fire Alarm Boxes > 907.4.2.5 Protective Covers
704.9 Fire and Smoke Protection Features, Impact Protection
Where the fire protective covering of a structural member is subject to impact damage from moving vehicles, the handling of merchandise or other ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 704 Fire-Resistance Rating of Structural Members > 704.9 Impact Protection