Where openings are required to be protected, fire doors
and fire shutters shall comply with Section 716.5
and fire window assemblies
shall comply with Section 716.6
Opening protectives are not required where the building is equipped throughout with an automatic sprinkler system
in accordance with Section 903.3.1.1
and the exterior openings are protected by a water curtain using automatic
for that use.