// CODE SNIPPET
18.104.22.168 Primary (Dry) Cell
Related Code Sections
22.214.171.124 Definitions, Primary (Dry) Cell
A nonrechargeable electrochemical cell requiring periodic replacement, such as a 9-volt alkaline cell. (SIG-FUN) ...
National Fire Alarm and Signaling Code 2019 of Maine > 3 Definitions > 3.3 General Definitions > 3.3.41 Cell > 126.96.36.199 Primary (Dry) Cell
188.8.131.52.1 Public Emergency Alarm Reporting Systems,
Float-charged batteries shall be of the storage type. Primary batteries (i.e., dry cells) shall not be used ...
National Fire Alarm and Signaling Code 2019 of Maine > 27 Public Emergency Alarm Reporting Systems > 27.5 Alarm Processing Equipment > 27.5.2 Alarm Processing Equipment at Communications Center > 184.108.40.206 Float-Charged Batteries > 220.127.116.11.1
14.3.1* Inspection, Testing, and Maintenance,
cell/unit if alarm equipment manufacturer's replacement date has been exceeded. (2) Primary (dry cell) other than those used in low-power ...
National Fire Alarm and Signaling Code 2019 of Maine > 14 Inspection, Testing, and Maintenance > 14.3 Inspection > 14.3.1*
23.16.2* Protected Premises Alarm and Signaling Systems, Power Supplies
A primary battery(s) (dry cell) that meet the requirements of 18.104.22.168 or 22.214.171.124 shall be permitted to be used as the sole power source ...
National Fire Alarm and Signaling Code 2019 of Maine > 23 Protected Premises Alarm and Signaling Systems > 23.16* Special Requirements for Low-Power Radio (Wireless) Systems > 23.16.2* Power Supplies
126.96.36.199.2 Special Occupancy Requirements, Wet, Dry, and Preaction Systems
Where each cell of the cooling tower is separated by a fire-resistant partition, the water supply shall be adequate to supply all discharge outlets ...
Standard for the Installation of Sprinkler Systems 2016 of Maine > 22 Special Occupancy Requirements > 22.21 Water Cooling Towers > 22.21.1 Design Requirements > 188.8.131.52 Sprinkler System Water Supply > 184.108.40.206.2 Wet, Dry, and Preaction Systems