(R) Prewiring for Generator Installation
- Circuit conductors shall be appropriately sized in relation to the anticipated load as stated on the label required in (R)(4).
- Where junction boxes are utilized at either of the circuit originating or terminus points, free ends of the conductors shall be adequately capped or taped.
- Where devices such as receptacle outlet, transfer switch, and so forth, are installed, the installation shall be complete, including circuit conductor connections.
- A safety label with the signal word WARNING in minimum 6-mm (1/4-in.) high letters and body text in minimum 3-mm (1/8-in.) high letters on a contrasting background shall be affixed on the cover of each junction box containing incomplete circuitry and shall read, using one of the following warnings, as appropriate:
WARNING GENERATOR ONLY INSTALL A GENERATOR LISTED SPECIFICALLY FOR RV USE HAVING OVERCURRENT PROTECTION RATED 110-125-VOLT AC, 60 HZ, _____ AMPERES MAXIMUM.
WARNING GENERATOR ONLY INSTALL A GENERATOR LISTED SPECIFICALLY FOR RV USE HAVING OVERCURRENT PROTECTION RATED 120-240-VOLTAC, 60 HZ, _____ AMPERES MAXIMUM.
The correct ampere rating shall be legibly marked in the blank space.