// CODE SNIPPET
M2003.1.1 Pressurized Expansion Tanks
JUMP TO FULL CODE CHAPTER
Pressurized expansion tanks shall be consistent with the volume and capacity of the system. Tanks shall be capable of withstanding a hydrostatic test pressure of two and one-half times the allowable working pressure of the system.
Related Code Sections
M2003.1.1 Boilers and Water Heaters, Pressurized Expansion Tanks
Pressurized expansion tanks shall be consistent with the volume and capacity of the system. Tanks shall be capable of withstanding a hydrostatic test ...
Residential Code 2018 of Kansas > 20 Boilers and Water Heaters > M2003 Expansion Tanks > M2003.1 General > M2003.1.1 Pressurized Expansion Tanks
M2301.2.8 Solar Thermal Energy Systems, Expansion Tanks
Expansion tanks in solar energy systems shall be installed in accordance with Section M2003 in solar collector loops that contain pressurized heat ...
Residential Code 2018 of Kansas > 23 Solar Thermal Energy Systems > M2301 Solar Thermal Energy Systems > M2301.2 Design and Installation > M2301.2.8 Expansion Tanks
1009.1 Boilers, Water Heaters and Pressure Vessels, Where Required
Expansion tanks shall be of the closed or open type. Tanks shall be rated for the pressure of the hot water system. Exception: Expansion tanks shall ...
Mechanical Code 2018 of Kansas > 10 Boilers, Water Heaters and Pressure Vessels > 1009 Hot Water Boiler Expansion Tank > 1009.1 Where Required
607.3 Water Supply and Distribution, Thermal Expansion Control
expansion control device shall be connected to the water heater cold water supply pipe at a point that is downstream of all check valves, pressure ...
Plumbing Code 2018 of Kansas > 6 Water Supply and Distribution > 607 Hot Water Supply System > 607.3 Thermal Expansion Control
M2003.2 Boilers and Water Heaters, Minimum Capacity
The minimum capacity of expansion tanks shall be determined from Table M2003.2. TABLE M2003.2 EXPANSION TANK MINIMUM CAPACITY a FOR FORCED HOT ...
Residential Code 2018 of Kansas > 20 Boilers and Water Heaters > M2003 Expansion Tanks > M2003.2 Minimum Capacity