// CODE SNIPPET
606.5.10 Pressure Relief for Tanks
JUMP TO FULL CODE CHAPTER
Every pressure tank in a hydropneumatic pressure booster system shall be protected with a pressure relief valve. The pressure relief valve shall be set at a maximum pressure equal to the rating of the tank. The relief valve shall be installed on the supply pipe to the tank or on the tank. The relief valve shall discharge by gravity to a safe place of disposal.
Related Code Sections
606.5.10 Water Supply and Distribution, Pressure Relief for Tanks
Every pressure tank in a hydropneumatic pressure booster system shall be protected with a pressure relief valve. The pressure relief valve shall ...
Plumbing Code 2018 of Kansas > 6 Water Supply and Distribution > 606 Installation of the Building Water Distribution System > 606.5 Water Pressure Booster Systems > 606.5.10 Pressure Relief for Tanks
18.104.22.168.2 Marine Systems,
Relief valves shall comply with 46 CFR 54.15-10 ...
Standard for the Installation of Sprinkler Systems 2016 of Kansas > 26 Marine Systems > 26.7 Water Supplies > 26.7.2 Pressure Tank > 22.214.171.124 Relief Valves > 126.96.36.199.2
P2804.3 Water Heaters, Pressure Relief Valves
Pressure relief valves shall have a relief rating adequate to meet the pressure conditions for the appliances or equipment protected. In tanks ...
Residential Code 2018 of Kansas > 28 Water Heaters > P2804 Relief Valves > P2804.3 Pressure Relief Valves
5705.2.1 Flammable and Combustible Liquids, Pumps
Where positive-displacement pumps are used, they shall be provided with pressure relief discharging back to the tank, pump suction or other approved ...
Fire Code 2018 of Kansas > 57 Flammable and Combustible Liquids > 5705 Dispensing, Use, Mixing and Handling > 5705.2 Liquid Transfer > 5705.2.1 Pumps
6004.2.2.5 Highly Toxic and Toxic Materials, Piping and Controls—Stationary Tanks
control on all tank inlet or outlet connections. Exceptions: Inlet connections designed to prevent backflow. Pressure relief devices ...
Fire Code 2018 of Kansas > 60 Highly Toxic and Toxic Materials > 6004 Highly Toxic and Toxic Compressed Gases > 6004.2 Indoor Storage and Use > 6004.2.2 General Indoor Requirements > 6004.2.2.5 Piping and Controls—Stationary Tanks